Apply Now for a GSHP Rebate
Who’s Eligible for a CMLP Rebate?
Ground-source heat pumps installed at new or existing buildings are eligible for rebates, though the system must be used for heating (in addition to heating use, systems may providing cooling as well). Projects with a single heat pump serving multiple units in a multifamily residential or multi-unit commercial building can apply jointly with one application, subject to existing caps. A single apartment or condominium can also apply individually. Projects must have rated heating capacity no greater than 10 tons (120 kBTU/hr).
Annual Rebate Caps
For each 12 month period, each residence is eligible for a maximum rebate of $3,125 per project site address at the base rebate level, $4,000 with the 120% Income-Based Rebate, or $7,500 with the 80% Income-Based Rebate. Each business is eligible for a maximum rebate of $6,250 per project site address. Customers may apply for more than one GSHP rebate over the life of the GSHP rebate program. However, a customer may receive only one GSHP rebate within a twelve month period. This policy is subject to change in the future.
Project installation may not commence until after the application has been approved by CMLP and the system owner has received an award letter. Projects that have already commenced construction are not eligible for the rebate.
Energy Assessment Requirement
All existing buildings must have an energy efficiency assessment completed within the past four years or have an energy assessment scheduled to occur and completed within six months of project completion. CMLP highly recommends that priority recommendations from the assessment be implemented before or in coordination with the installation of the GSHP. Making a building more energy efficient can reduce the size and cost of the GSHP needed to heat and cool your building.
Households heating with natural gas can contact MassSAVE at (866) 527-SAVE (7283) or masssave.com/en/saving/energy-assessments/ for an assessment. Businesses heating with natural gas can find information about Mass Save facility assessment at https://www.masssave.com/en/saving/business-rebates/facility-assessments/
All others can sign up with Energy New England at firstname.lastname@example.org, (888) 772-4242, or ene.org/residential-audits/. Energy New England, CMLP’s energy assessment provider, provides no-cost home energy assessment, and business energy assessment at a 50% discount. CMLP covers 50% of the cost of a full-scale business energy assessment.
New buildings do not require energy assessment, although energy assessment are still recommended.
Rebate Type Eligibility
Rebate levels for GSHP systems are calculated per heating ton (12,000 BTU/hr). Residential rebates are limited to the first five tons of heating capacity per housing unit. Non-residential entities can receive funding for up to ten tons of heating capacity through this program. Income-based rebates are available for qualifying residential applicants.
If the project meets the above eligibility requirements, system owners should next determine which rebate type they are eligible for based on the following table:
Income-Based Thresholds by Household Size
$625 per 12,000 BTU/hr**
(up to a maximum rebate of $6,250)
|Residential Rebate Type|
Annual Gross Income
Available to all households meeting project requirements (see above).
$625 per 12,000 BTU/hr**
(up to a maximum rebate of $3,125)
|120% Income-Based Rebate*|
Available to all households that meet project eligibility requirements and have verified that their income is below 120% of the Massachusetts state median income.
$800 per 12,000 BTU/hr**
(up to a maximum rebate of $4,000)
|80% Income-Based Rebate*|
Available to all households that meet project eligibility requirements and have verified that their income is below 80% of the Massachusetts state median income.
$1,500 per 12,000 BTU/hr**
(up to a maximum rebate of $7,500)
*To receive an income-based rebate, the customer must complete one of the accepted income verification methods. Please see the “How Do I Qualify for an Income-Based Rebate?” question below for more information about income-based rebates and income verification.
**For the purposes of determining rebate levels for GSHPs, CMLP uses the American Heating and Refrigeration Institute’s (AHRI’s) heating capacity for the system.
How do I participate in CMLP’s GSHP rebate program?
All applications must be submitted and approved by CMLP prior to starting project construction, and, to be eligible for a rebate, construction must not commence until an award letter is issued. Once the system owner has decided to move forward with the project, the installer should apply for a rebate on the system owner’s behalf.
Step 1: Find an Installer
First, select a GSHP installer, who will submit the rebate application on your behalf.
The following resources can help you identify potential installers:
- The Massachusetts Clean Energy Center, which administers a GSHP rebate program primarily in communities without municipal light plants, maintains a list of installers who have previously participated in their program. Go to http://www.masscec.com/ground-source-heat-pump-installers to download the list. Using an installer from this list is NOT required to receive a CMLP rebate.
- The following directories can also help you identify installers:
In order for your GHSP installation to be eligible for a CMLP rebate, the following conditions must be met:
- Your installer must actively hold one of the following credentials:
- International Ground-Source Heat Pump Association (IGSHPA) Accreditation;
- Certification as a GeoExchange Designer (CGD) from IGSHPA; or
- Professional Engineer (“PE”) License from the National Society of Professional Engineers.
Your installer must submit a copy of the certificate for one of the accreditations listed above with the rebate application.
If not currently holding one of these credentials, your installer must provide references for three GSHP installations, including phone numbers and email addresses for each reference. Rebate approval is contingent upon a successful reference check. Installers must achieve one of the above credentials within one year of submitting their first GSHP rebate application to CMLP in order to be eligible to submit further GSHP rebate applications to CMLP.
2. Your installer must agree to fix any system defects or significant workmanship issues identified during the first year after the project completion date.
CMLP recommends that our customers:
- Review the material at the “How can I learn about the best ground-source heat pump options for my home?” and “What questions should I ask potential installers?” listed above.
- Solicit proposals from at least three installers.
- Ensure that installers have one of the credentials listed above.
- Check references from prior installations.
Step 2: Select Eligible Equipment
In order to be eligible for a rebate, projects must meet the following requirements:
A. Equipment Requirements
- The GSHP must be AHRI rated.
- Eligible heat pumps must have AHRI-rated COP (Coefficient of Performance) and EER (Energy Efficiency Rating) equal to or greater than the following:System TypeCooling EERHeating COPWater-to-AirClosed Loop Water-to-Air17.13.6Open Loop Water-to-Air21.14.1Water-to-WaterClosed Loop Water-to-Water16.13.1Open Loop Water-to-Water20.13.5Direct ExchangeDirect Exchange16.03.6
a. In the application, EER and COP must be calculated using the following equations:
i. EER = (full load EER + part load EER) / 2
ii. COP = (full load COP + part load COP) / 2
b. EER and COP figures for the above calculations must use the AHRI rated ground loop heat pump (GLHP) figures for closed-loop systems and the AHRI rated ground water heat pump (GWHP) figures for open-loop systems.
3. GSHP systems must be designed with full-load heating capacity between 90% and 120% of peak heating load (BTU/hr for heating) according to the applicable heat load calculation. On a case-by-case basis, CMLP will consider eligibility of GSHPs installed at buildings with heating capacity sized below 90% of peak heating load if designed to operate in conjunction with back-up or peaking heating systems.
4. All GSHP systems must be installed by licensed contractors and/or plumbers in accordance with the National Electric Code and manufacturer’s specifications and must conform to all applicable municipal, state, and federal codes, standards, regulations, and certifications, as well as program requirements. At a minimum, a contractor must possess an EPA 608 license to handle refrigerant and an electrician license to complete the electrical work on the heat pump.
5. Blower motors must be multi-speed or variable-speed, high-efficiency motors. Motors qualify as “energy-efficient” if they meet or exceed the efficiency levels listed in the National Electric Manufacturers Association’s (“NEMA’s”) MG1-1993 publication. Single-stage water-to-water console units with a capacity less than 2 heating tons are eligible to be preapproved by CMLP, provided these types of units satisfy all of the other eligibility requirements described herein.
6. Systems must meet ANSI/AHRI/ASHRAE/ISO Standard 13256-1 for water-to-air models, Standard 13256-2 for water-to-water models, or AHRI Standard 870 for DX models.
7. All compressors must use two-stage, multi-speed, or variable-speed drives, unless they are water-to-water units. Single-stage water-to-water systems are allowed, provided they include accumulator tanks with the greater of ten gallons of capacity per heating ton or industry/manufacturer recommended best practice.
8. All GSHP systems receiving a rebate from CMLP must be covered by a minimum five-year manufacturer’s warranty.
9. CMLP may submit open-loop, horizontal-loop, and direct exchange system designs to a third-party consultant to evaluate a project’s design and reserves the right to submit designs of other system types for review. Installers should be prepared to work with the reviewer to answer any outstanding questions about the project’s design and must respond within seven days to any information requests.
B. Well Requirements
10. Vertically bored closed-loop projects must have a minimum depth of 150 feet per 12,000 BTU/hr of heating load served by the system (i.e., the lesser of capacity and peak load). Capacity must be determined using the method used to calculate rebate values (see Section A. 2. a under Step 2). This must be sufficient to maintain a minimum entering water temperature of at least 30°F, with a recommended best practice of at least 32°F. Direct Exchange (DX) systems require a minimum of 120 feet of borehole depth per heating ton.
11. Closed-loop bore grouting must have a grout conductivity equal to or greater than anticipated earth conductivity of the drill site up to 1 BTU/hr-ft-°F.
12. There must be at least 15 feet of separation between closed-loop bore holes.
13. All projects must comply with the MassDEP Bureau of Resource Protection Drinking Water Program, Guidelines For Ground Source Heat Pump Wells, and Underground Injection Control Program (December 2013, which may be amended from time to time) found at www.mass.gov/eea/docs/dep/water/laws/a-thru-h/gshpguid.pdf
C. Open Loop Requirements
14. All open-loop GSHP wells shall be installed in conformance with MassDEP’s Private Well Guidelines (www.mass.gov/eea/docs/dep/water/laws/i-thru-z/prwellgd.pdf) (as amended) or MassDEP’s Guidelines and Policies for Public Water Systems (www.mass.gov/eea/docs/dep/water/laws/a-thru-h/glintro.pdf) (as amended), whichever is applicable. All GSHP wells shall be installed in conformance with 313 CMR 3.00: Certification of Well Drillers and Filing of Well Completion Reports (http://www.mass.gov/eea/docs/dep/service/regulations/310cmr46.pdf)
a. Open loop systems must register for a permit with the Massachusetts Department of Environmental Protection (“MassDEP”)’s Underwater Injection Control (UIC) program. The UIC registration number must be noted on the Project Completion Form at the time of project completion. Open loop systems installed on parcels of land used for single-unit residences are exempt. (https://www.mass.gov/underground-injection-control-uic)
15. A standing column well must include a bleed circuit and drywell to maximize thermal efficiency based on available water production
16. Applications for open- and horizontal-loop systems must explain the method for determining pressure and flow rate.
D. Horizontal-Loop Project Requirements
17. The Application must include the file from the horizontal-loop design software showing inputs and system design specifications.
E. Direct Exchange System Requirements
18. Direct exchange (DX) heat pumps, which circulate a refrigerant through a closed-loop copper pipe system (whereas most systems utilize plastic pipes that circulate water or a water antifreeze mixture), must meet the following additional conditions:
a. DX wells require cathodic protection ensuring a minimum expected well life of 20 years.
b. DX System Owners must certify that they will undergo an end-of-life decommissioning that includes full refrigerant recovery11
d. The refrigerant must be R-410A. If the installer intends to use a different refrigerant type, CMLP will consider it when then application is submitted.
e. The entire well depth interval for DX wells shall be grouted with thermally enhanced grout that achieves hydraulic conductivity of 10-7 centimeters per second or less (per MassDEP).
f. A permanent placard must be attached to the heat pump unit, detailing:
i. Loop field refrigerant content, type, and volume;
ii. Loop locations description;
iii. Loop piping material;
iv. Required maintenance schedule on loop field, refrigerant, and heat pump; and
v. Planned decommissioning date and process, consistent with loop field useful life.
g. The installer must provide a detailed operational handbook for the System Owner that provides an overview of system design, operations, and the information stated in 18.b. above.
F. Heat Load Calculation Requirements
19. Equipment must be sized with a building peak heating capacity (BTU/hr) calculated using the Air Conditioning Contractors of America (“ACCA”) Manual J (for residential) or Manual N (for commercial) building heat load calculation method.
20. Installers must submit the summary page of the applicable heat load calculation of the building’s peak heat load at the 99% dry bulb heating design temperature for the most relevant ACCA location. Heating set temperatures may be between 68 and 72 degrees Fahrenheit.
21. CMLP strongly recommends all projects incorporate system performance monitoring technology to help owners understand performance throughout the year.
CMLP may choose to monitor a subset of systems installed under this program. To be eligible for a rebate under this program, the system owner must agree to allow metering and monitoring to be conducted on their project for up to twenty-four (24) months after installation, if requested. The system owner will be required to submit fossil fuel bills for two (2) years prior to installation (for existing buildings) and for the duration of the performance monitoring. Monitoring equipment would be paid for and installed directly by contractors to CMLP with no direct cost to the system owner. Data would be collected and analyzed for program evaluation purposes and will not impact the rebate received by the system owner.
H. Deviation from Requirements
Although CMLP typically does not allow deviation from these design requirements, certain site characteristics may lend themselves to alternate system designs. If for technical reasons, a design requirement cannot be met for an installation, the installer may request a waiver. All variations must be explained in detail in the Project Notes field at the bottom of the application, and output from geothermal modeling software must be submitted. CMLP may send these applications to CMLP’s third party consultant for review and consideration.
I. Other Project Requirements
Installed systems must meet all applicable state and local laws and ordinances, including applying for and receiving a building permit and, upon project completion, receiving sign-off from a local building authority.
Step 3: Apply for a Rebate
Prior to deciding to move forward with a system, residents should determine if they are eligible for the Income-Based Rebate, as described under the “Who’s Eligible for a Rebate?” question above. For example, a household of four with annual income of $132,230 or less may qualify. If eligible, complete one of the three income verification methods described in the “How do I qualify for an Income Based Rebate?” question below.
Once the system owner has decided to move forward with the project, the installer should complete and submit the application on the system owner’s behalf, with the assistance and approval of the system owner. Application documents must be emailed to email@example.com. To expedite the review, please include “GSHP Application: [Project Site Name]” in the subject line. Both the installer and system owner should review all information before submitting it to CMLP.
All applications must be submitted and approved by CMLP prior to starting project construction, and, to be eligible for a rebate, construction may not commence until an award letter is received.
All complete applications must include:
1. Application Form: A completed Excel Application Form
a. Energy Assessment: Date of completed or scheduled energy assessment must be noted on rebate application. Assessments performed through CMLP’s energy assessment program, Concord’s Green Your Heat Program, the MassSave program or other energy assessment providers are all accepted.
i. If you believe you had an assessment in the last four years through CMLP, but do not know the date, contact Energy New England, CMLP’s energy assessment provider, at 1-888-772-4242 for assistance.
ii. If you believe you had an assessment in 2015 or 2016 through Concord’s Green Your Heat Program, but do not know the date, contact CMLP’s Energy Specialist Pamela Cady at firstname.lastname@example.org or 978-318-3149 for assistance.
iii. For the date of a MassSave assessment, call 800-632-8300.
2. Contract: Installation contract signed by both the system owner and the installer
3. Electric Bill: A copy of a recent electric bill from the project site. New construction projects can submit the electric bill or a request for electric service at project completion.
4. Heat Load Calculation: The summary report from the Manual N (commercial) or Manual J (residential) calculation of the building heat load, as described in Section F under Step 2: Select Eligible Equipment.
5. AHRI Rating Certificate: A copy of the Air-Conditioning, Heating, and Refrigeration Institute (“AHRI”) rating certificate for each heat pump model installed.
Certain projects must also submit additional documents, as follows:
1. Income Verification: Residential Income-Based Rebate eligibility verification (if applicable). Eligibility thresholds and income verification methods can be found under the “How do I qualify for an income-based rebate?” question below.
2. Tax Documentation (if applicable) –
- Residential system owners do not need to submit W-9 forms or other tax documentation.
- All non-residential system owners (including all tax-exempt and government entities) must submit signed W-9 forms, as do any installers listed as Payees.
3. Design Reports: Horizontal-loops systems (if applicable) – Software design report showing all system inputs.
4. Flow Rate: Open-loop systems (if applicable) – Detailed estimation of well water flow rate.
5. Modeling Summary: Non-residential systems (if applicable) – Modeling software summary page.
Rebates can be paid to the system owner or to the installer, provided that the system owner provides written permission in the application. If the application meets all requirements of this program and funding remains available, CMLP will issue the rebate payment to the payee via mail.
The rebate may be combined with any other local, state or federal incentives, and applicants are encouraged to do so where possible. CMLP will not provide funding that would, in CMLP’s sole determination, exceed total project costs. Total project costs shall include all costs presented in the application, less all other available incentives, including any state or federal rebates, subsidies, and tax incentives, discounted to present value where necessary. CMLP will evaluate these situations on a case-by-case basis, and reserves the right to reduce any award projected to exceed total project costs by an amount sufficient to prevent the excess.
The Town of Concord assumes no liability for any equipment, installation or damages, and may inspect equipment to verify the above information at any time up to 1 year after receiving the rebate application.
Step 4: Receive Rebate Award Letter
Upon receiving the application, CMLP staff will send two separate emails. The first email will confirm that the application has been received; the second email will indicate one of the following statuses:
- the application is complete;
- the application is incomplete and further information is needed; or
- the proposed project is ineligible and has been rejected.
Applications will be evaluated to ensure that the project will meet the eligibility and project requirements described above. CMLP reserves the right to accept, assign design reviews, or reject applications based on completeness, qualitative criteria, and available funding; to make no awards; to award less than the applicant requests; and/or to award less than the maximum amount of funds potentially available through this program. If CMLP elects to conduct a design review, the installer must be prepared to answer the reviewer’s questions about the project’s design and must respond within seven days to any information requests.
CMLP will notify applicants of their application status within four weeks of receipt of a complete application, barring extenuating circumstances. If the application meets all requirements of this program and funding remains available, CMLP will issue an award letter to the system owner and installer via email that will provide details on the award amount and, among other pertinent information, state which party will receive payment (the “payee”). CMLP will also attach a Project Completion Form, which will be submitted to CMLP upon project completion.
Step 5: Complete Project:
Project installation may commence only after receipt of the award letter. Projects must be completed within six months of the award date on the award letter for projects at existing buildings and within twelve months for projects at new construction buildings.
Upon project completion, the installer in cooperation with the system owner will complete and submit supporting documentation to CMLP, including:
1. Project Completion Form; and
2. Completed GSHP manufacturer or distributor start-up sheet. This documentation should be submitted by email to email@example.com with “GSHP Project Completion: [System Owner Name (residential) /Site Name (non-residential)]” in the subject line.
Step 6: Receive Rebate Payment:
Rebates can be paid to the system owner or installer, provided that the system owner provides permission in the application. Upon approval of the project completion documentation, payment will be issued to the designated payee within 4 weeks, barring extenuating circumstances.
In the interest of increasing access to ground-source heat pumps to all residents of Concord, CMLP offers additional incentives for households with income below 80% or 120% of the state median income. Eligibility thresholds are determined based on household size. Eligibility for the income-based rebate is based on the income of the system owner’s household.
Eligibility is based on total household income (Tax Return Form 1040, line 6), as determined by the system owner and household members’ federal income tax filings for the most recent year available. Each system owner household is only eligible to receive the income-based rebate at one residence.
Income-Based Rebate Adder Thresholds by Household Size
80% of State Median Income
120% of State Median Income
To receive the Income-Based Rebate, the system owner must complete one of the following three income verification methods:
1. Electric Bill: When submitting the application documents, provide CMLP with a copy of an electric bill from within the last 6 months showing a Residential Assistance Credit.
2. Fuel Assistance Letter: When submitting the application documents,provide CMLP with a copy of a fuel assistance letter of acceptance from the past 12 months showing the date, system owner’s name, and project site address.
3. Income Verification: Prior to submitting application documents,request income verification from CMLP by mailing the Income Verification Request Form and the first two pages of the most recent federal IRS tax return form 1040 (showing line 6) for each adult filing (single, married filing jointly, married filing separately, and/or head of household) within the household to Attn: Pamela Cady at CMLP, P.O. Box 1029,Concord, MA 01742 or by hand delivery to CMLP’s Operations Center at 1175 Elm St, Concord. All tax information provided to CMLP will be shredded upon completion of income verification.
You will be notified by email or postal mail once your eligibility for an income-based rebate has been determined. Include this proof of income verification with your application documents.
Does CMLP offer a special electric rate for heat pump users?
CMLP offers the R-7 “Electric Resistance & Heat Pump Heating Systems/DHW” rate for heat pump users, a special winter rate designed to prevent an unintended spike in electricity charges for electric heating customers as a result of CMLP’s tiered rate structure. This rate may benefit you if you already use more than 600 kilowatt-hours in some winter months, or if you expect to do so once your heat pump is installed.
However, In order to take advantage of this rate, you must request that a separate meter be installed by CMLP. This meter will record the electric usage of your heat pump. Electricity use recorded on this meter from October 1st through May 1st will be subtracted from the normal billing meter and billed at $0.14431 per kWh. From May 2nd through September 30th, the use through this meter will be billed under the regular R-1 Rate, which ranges from the tier 1 rate of $0.14431 to the tier 3 rate of $0.18685 per kWh, depending on how much electricity your household has used that month. CMLP’s R-1 rate schedule describes how your electric rate changes depending on how much electricity your household uses in a given month.
CMLP will supply and install the separate meter at no cost to you. However, you will need to pay an electrician to install a meter socket for the new meter. An additional electrical panel is typically needed as well. Costs for a meter socket / electrical panel can range from $1,000 to $4,000. The time it will take you to recoup the cost of the new meter socket/panel through electricity cost savings depends on several factors:
- the socket / panel installation cost;
- the extent to which your electric usage will exceed 600 kWh per month once your heat pump is installed and
- how long the tiered rate structure and the Electric Resistance & Heat Pump Heating Systems/DHW rate remain in effect. CMLP’s staff has made a recommendation to the Light Board that the tiered rate structure be eliminated. If the Board votes to do so, the Electric Resistance & Heat Pump Heating Systems/DHW rate will no longer be needed to prevent unintended spikes in electricity charges for heat pump users, and will also be eliminated. In that case, it is unlikely that you’d recoup your investment in a new meter socket and electrical panel through electricity cost savings.
Please note also that customers who have a solar array usually expect that solar electricity will lower the portion of their electric bill attributable to the electricity needed to power their heat pump during the winter. However, if a heat pump is separately metered so that a customer can receive the Electric Resistance & Heat Pump Heating Systems/DHW rate for winter usage, CMLP is unable to offset the winter usage measured by the separate meter with solar electricity generated by the array. Therefore, having a solar array will not lower a customer’s winter bill for heat pump electricity usage if the Resistance & Heat Pump Heating Systems/DHW rate is in effect. During the summer, when the Resistance & Heat Pump Heating Systems/DHW rate does not apply, solar electricity will offset the portion of an electricity bill due to a heat pump being used for air conditioning, even if the heat pump is separately metered.
Further, heat pump customers with solar would need to locate the second meter next to the existing house meter in order for the solar electricity powering the heat pump to be accounted for properly. This can require longer wire runs that increase the cost of the meter socket installation.
Please consider these factors when deciding whether to invest in a separate meter/electric panel.
If you have further questions about the Electric Resistance & Heat Pump Heating Systems/DHW rate, please contact Carole Hilton, Customer Service Coordinator, at (978) 318-3158 or CHilton@concordma.gov.
Are there other incentives or tax credits available to lower the cost of purchasing a ground source heat pump?
- Federal Tax Credit. Homeowners and businesses are able to claim a federal renewable energy investment tax credit (ITC) of up to 30% of the cost of a GSHP system (excluding cost of ductwork modifications) when installation begins in 2019. The ITC then steps down to 26% for projects that begin construction in 2020 and 22%for projects that begin in 2021. After 2021, the residential credit will drop to zero while the commercial credit will drop to a permanent 10%.
- Alternative Energy Credits. If your GSHP is your only heating source, you are eligible to receive and sell Alternative Energy Certificates (AECs), which are awarded to owners of clean heating & cooling technologies through the Commonwealth’s Alternative Portfolio Standard (APS). The number of certificates you receive will be based on a variety of criteria, including the size and efficiency of your home (e.g. if your home has a HERS rating under 50 or is a "Zero Energy" Home or Passive House).
Depending on these factors—and the value of the AECs at quarterly auctions, you could receive a total of $3,500 to $11,000+ over the lifetime of a GSHP system. Owners of GSHP systems may choose to receive 10 years-worth of AECs upfront (“pre-minting”) rather than on a quarterly basis, effectively turning the APS into upfront rebate program. If this option is pursued, no additional AECs will be issued after the upfront “pre-minting.”
An Excel calculator developed by the Dept. of Energy Resources is available here. Please note that a default AEC value of $20/MWh is assumed in this calculator. We would recommend using a more conservative estimate of $15/MWh or lower to represent a lower auction value of these AECs and an aggregator fee of about 7% or more.
Speak with your installer to learn more about the AEC’s and the incentive you could receive for your system.
- Sales Tax Exemption. GSHP systems are exempt from the Massachusetts state sales tax.
Who can I contact if I have more questions about CMLP’s ground-source heat pump program?
Contact Jan Aceti, CMLP’s Energy Conservation Coordinator, at firstname.lastname@example.org or 978-318-3151.
11 If the system is not decommissioned at the end of its useful life, the refrigerant is ultimately likely to leak out of the pipe, causing it to evaporate and escape into the atmosphere. The most common refrigerant for modern DX systems is R-420, a greenhouse gas with over 2,000 times the global warming potential of CO2.